12V SINGLE OUTPUT TRANSFORMERS WARNING BE SURE THE ELECTRICITY TO THE WIRE YOU ARE WORKING ON IS SHUT OFF EITHER THE FUSE REMOVED OR THE CIRCUIT BREAKER OFF Use of other manufacturers components will void warranty UL listing and create a potential ID: 35374 Download PdfTags :
Download Pdf - The PPT/PDF document "AMBIANCE ACCENT LIGHTING SYSTEM INSTRUCT..." is the property of its rightful owner. Permission is granted to download and print the materials on this web site for personal, non-commercial use only, and to display it on your personal computer provided you do not modify the materials and that you retain all copyright notices contained in the materials. By downloading content from our website, you accept the terms of this agreement.
Presentation on theme: "AMBIANCE ACCENT LIGHTING SYSTEM INSTRUCTIONS FOR ASSEMBLY AND INSTALLATION OF THE AMBIANCE ACCENT W AND W"— Presentation transcript
ACCENT LIGHTING SYSTEM INSTRUCTIONS FOR ASSEMBLYAND INSTALLATION OF AMBIANCE ACCENT 150W AND 300W. 12V., WARNING: BE SURE THE ELECTRICITYTO THE WIRE YOU ARE WORKING ON CIRCUIT BREAKER OFF.void warranty, U.L. listing and create a potential WARNING: THIS TRANSFORMER IS FOR INDOOR USE ONLY. ransformer Installation Select desired location to mount SSlighting system to achieve the most efficient operation. Use MOUNTING BRACKETS on SSAfter firmly mounting the SSlisted CONNECT not furnished not furnished of ELECTRICALSUPPLYCABLE at site. Remove cover anddesired KNOCKOUTS from SSCONNECTOR.To control transformer, install ON/OFF switch or good qualityline voltage dimmer on 120V side of transformer.Connect SUPPLYGROUND TO STUD, insideTRANSFORMER CASE with HEX NUTwith INTEGRALLOCKWASHER. Connect wire marked ÒcommonÓ on Ò120 voltÓ or ÒBoostÓ to black supply wire ( cap off the unusedvoltage is below 110V or the transformer is mounted in aaway. Refer to back of this page for remote installation detail.Select another U.L. listed CONNECT not furnished not furnished appropriate to the type of CONDUITor Ambiance cables andOR to TRANSFORMER CASE. SlipCONDUITor cables into TRANSFORMER CASE and secureConnect Ambiance low voltage cables or extension wires toires marked ÒX1Ó and ÒX 2Ó in transformer. Use U.L. listed WARNING: DO NOT ENERGIZE ELECTRICALSUPPLYCIRCUIT TSSALLCONNECTIONS HAVE BEEN MADE ANDTESTED ACCORDING TO NATIONALELECTRICALCODES AND ALLLOCALELECTRICALCODES. IF YOU ARE UNCLEARHOW TO PROCEED, CONTACT A FIG 1 NOTE: Each low voltage cable from the transformer must see back for detail see back for detail Install COVER on TRANSFORMER CASE and secure inplace with COVER SCREW. 1. 12/2 Ambiance cable is suitable for 12V only, for2. 10/2 Ambiance cable is suitable for 300W maximum3. Wattage load must be minimum of 50% of MOUNTTHIS END CONNECTORS120V. ÒINÓLOWVOLTAGE MOUNTING BRACKET ORS X1, X2X1, X2 VOLTAGE INSTALLATION AND SAFETYINSTRUCTIONS REMOTE TRANSFORMER INST ALLA TION For Transformer mounted remotely ( over 20 ft. from lighted use the wire selection chart below use thetap ). The boost tap will generate a higher output to compensate forthe lighting system.Proper selection of the cable size between remote See chart below See chart below FIG 2 DONOT exceed 90% of rated transformer wattage Use U.L. listed Junction Box and U.L. listed Terminal Block MAXIMUM WATTAGE BASED ON 10% LINE LOSS, WIRE LENGTH AND SIZECALCULAORORT FIRST SOCKET ON SYSTEM FROM TRANSFORMER TO FIRST SOCKET, FROM EACH OUTPUT MUST NOT USE BOOST TAP, TO PREVENT OVERVOLTAGE AT FIRST SOCKET2X12=2 PARALLEL RUNS OF 12 GUAGE CABLE. NOT FOR USE WITH 9481 2 AMBIANCE CABLE UNCTION BOX WIRE INSTALLATION AND SAFETYCONTINUEDCONTINUED INSIDECABINET INSTALLATION 1. Drill diameter hole or notch surfaces where cable will berunning through shelving or cabinet partition.NOTE: Low Voltage Ambiance Cable must be covered in SeaGull Lighting Sleeving (#9430) or track and cover (#9435 ⓟ).#9427 & #9428 etc.#9427 & #9428 etc..3.Do not install lampholder closer than 1 to closed ends (wallsurfaces, partitions etc.).4.Do not install more than 20 watts per cubic foot of cabinet airspace.5.Be sure not to decrease the free air space inside the cabinet. LAMPHOLDER ARTMENTILLUMINATEDILLUMINATED SECTIONILLUMINATED FIGURE 3FIGURE 4 TRACK/CABLE INST ALLA TION surfaces. DONOTNAILOR SCREW THROUGH CABLE TOATTACH TO ASURFACE. Use 9430 sleeving to cover wireEach Ambiance cable from the transformer to the point where FIG. 2 FIG. 3 between illuminated sections must be protected fromdamage. Enclose the cable in these areas with track andcover or listed conduit. 24V SYSTEM. INSTALL CABLE SO THAT CAUTION PRINTEDCAUTION: THE LOCATION AND NUMBER OF TRANSFORMERSCIRCUIT BREAKER WITH A BREAKER RATED FOR HIGH